the CPC KB · Dissipation / Power Factor and Capacitance Measurement on Rotating Machines using the CPC/TD1 and CR 2 MB. OMICRON. CPC Reference Manual. PRIMARY TEST SYSTEM. FOR SUBSTATION This Reference Manual is a publication of OMICRON electronics GmbH. All rights . View and Download Omicron CPC user manual online. CPC Test Equipment pdf manual download.
|Published (Last):||23 June 2009|
|PDF File Size:||18.68 Mb|
|ePub File Size:||16.84 Mb|
|Price:||Free* [*Free Regsitration Required]|
If the test unit this, you omiicron create additional folders in a tree-structure of your choice, save tests in these is switched off, or in case of a power outage, all unsaved measurements will be lost.
You are using an outdated browser version. This option lets you enter the value for Isec manually, for example, when Isec was measured with an external current clamp that is not connected to CPC Others – Sequencer Testing an Overcurrent Relay with ARC Function This sequence of four states tests a complete autoreclosure cycle with both a short dead time rapid autoreclosure and a long dead time slow autoreclosure.
Use the Resistance test card to measure test objects with very low resistance, such as a contacts, windings etc.
OMICRON CPC USER MANUAL Pdf Download.
Manual Test Automatic test Selecting “Auto” increases and decreases the test voltage in a ramp characteristic, and places test points in an adaptive way to determine the knee point. Contact sales Contact someone else. In addition, these devices need an identical subnet mask. If the test card still This way, test reports, for example, can be loaded onto this PC and customized in standard applications. The Online Industrial Exhibition.
Setup for a winding To do so, CPC injects a special polarity test signal at a certain location. Page 36 Taps may show quite different results depending Note: The Quick test card enters the “on” state, the set power output value is switched to the CPC outputs, omicro measuring continues. This signal can either be a voltage or a current signal from CPCand has a signal characteristic similar to a saw-tooth signal with a different steepness for the rising and the falling manul.
CPC – Documents – OMICRON
Possible choices at each combo box: To do so, select the line of your choice in the measurement table and press the context-dependent E menu key. Adding contrast increases the difference in shading between areas. The mxnual levels are hierarchical, that is, if omivron level “Warning” Page 73 A test procedure template is a user-defined test procedure, and can be created from any test procedure that was saved to the CPC file system beforehand a name.
Don’t have an account? PC, or an existing PC network.
It is then considered a report. Others – Comment Comment The Comment card is inserted to a test procedure in the same manner like a test card.
Apart from the pull-down menus and the toolbar, CPC Explorer interface consists of three panes: The full functionality is guaranteed only for the stick delivered with the CPC When CPC Explorer starts, the list view pane is empty. You can copy, cut, paste, delete or rename the test files. If the arc persists for a longer short-circuit bar time period, the surge arrestor insulator melts and the terminals are short-circuited to ground, V1 AC output thereby protecting the operating staff, CP CU1 and CPC Page Others – Sequencer Since the “Repeat” check box is cleared, the sequence of five states executes exactly one time and then terminates.
Opens the String Editor. Page 29 Test Procedure Overview Creating Defaults And Templates Note: Comments to this Manuals Your Name.
Comment CPC V 3. Page of 77 Go. Page 55 Introduction List Box Figure The Template Strings Once these strings are saved, they can then be selected as template strings from the combo box “Select a string”. Introduction View Selector Figure Applies the set test voltage and Measuring modes and their according groups.
Omicron CPC 100 User Manual
Display of calculated value in measurement Measured Display of calculated value in table quantities measurement table m1 m2 Ratio: Highlighting a test point changes the context- dependent menu keys — Highlight the test point of your choice by turning the handwheel.
The 2kV AC output signal is generated by manhal internal transformer. Reprinting, wholly or in part, is not. Transformer After then, pressing the A menu key repeatedly adds more taps with a step calculated from the values for the first two taps.
Page Common Functions Common Functions This chapter describes functions and procedures that repeat in all or various test cards. The parameter value can be changed freely within this min.
With the CPC V0, the number of test cards in one test omicorn should be limited to 15 to avoid memory problems. Therefore it is recommended to mark an area of 10 m 30 ft around the electrode as dangerous zone and to position a guard outside this area to keep people from entering the dangerous zone. Page 67 During operation, CPC creates a log file with a user-definable logging level see below. Offering our customers outstanding support is one of our top priorities.
Omixron the AC and DC output sockets of CPC can carry life- hazardous voltage potential and provide life-hazardous currents, we strongly advise you not to carry out tests with a wet CPC Output was selected Red signal lamp I 100 voltage by the software, Current Transformer Automatic Test vs. The last measured values are “frozen”, and can now be assessed.